Houses in multiple occupation (HMO)
HMO fire safety
Fire detection and fire safety requirements
We assess HMOs to make sure appropriate fire safety and detection systems are in place. The Regulatory Reform Act (Fire Safety) Order 2005 means that the landlord, or responsible person in charge of a HMO, must take reasonable steps to reduce fire risk and make sure people can escape if there is a fire.
For HMOs with one or two floors
The fire detection system must meet BS5838 Part 6 LD2 Type D1 (tamper proof battery back-up) or D2 (replaceable battery back-up). The system must include:
mains operated interlinked smoke detectors in the entrance, hallway, living areas and landing areas
an interlinked fixed temperature heat detector in the kitchen
sound, close-fitting traditional construction doors or fire doors fitted on all doors that open onto the main route of escape. Not hollow panel doors
a fire blanket compliant to BS EN:1869 in the kitchen
mortice rim locks or ‘quick release latches’ fitted to the entrance door, and any other door opening on to the main route of escape. Key operated locks are not acceptable
For HMOs with three or more floors
Larger HMOs will need extra fire safety and detection measures, such as fire doors. Some HMOs may need emergency lighting depending on the level of natural and artificial light.
Fire risk assessments
The landlord or responsible person in charge of any size HMO must provide a written fire risk assessment. They must update this assesment regularly.